A.Sean Kenney responds: Whenever I go on a residential service call where the power is out in a receptacle or a portion of a room, 75% of the time the problem is caused by a failed push-in terminal on a receptacle or switch.
Push-in terminals are small copper spring clips that only make contact with a small portion of the wire. When a push-in terminal is subjected to a high-amperage draw, the terminal often overheats, eventually causing the connection to burn out. Another problem is that when the electrician pushes the receptacle or switch into the box, the wires...
to continue reading